ALE111-S50-S1 |Yokogawa Ethernet Communication Module
GENERALThis document describes about Model ALE111 Ethernet Communication Module (for FIO) that a field control station (FCS) uses to perform Ethernet communication with subsystems such as FA-M3. This Ethernet communication module can be mounted on field control units (AFV30£, AFV40£, AFV10£, and AFF50£), ESB bus node unit (ANB10£), optical ESB bus node unit (ANB11£), and ER bus node unit (ANR10£).
able Ethernet communication module hardware specificationsItemSpecifications
Physical layer interfaceIEEE802.3 10BASE-TConnection methodPoint-to-pointConnectorRJ-45Transmission methodHalf-duplexTransmission speed10 MbpsTransmission route100 ohm twisted-pair cable (not shielded)Transmission distance1 segment, 100 m (in between FCS and subsystems, or HUB and subsystems)Installation methodMounted on ANB10£, ANB11£, ANR10£, AFF50£, AFV10£, AFV30£, or AFV40£No. of portsOne portMedia access controlCSMA/CDCommunication functions Communications with FA-M3, Modbus, MELSEC, YFGW, DARWIN/DAQSTATION, and PLC-5/SLC500Current consumption0.5 AWeight0.3 kg
OPERATING ENVIRONMENTHardware RequirementsThe Ethernet communication module runs on the following FCS. AFV30S, AFV30D, AFV40S, AFV40D, AFV10S, AFV10D, AFS30S, AFS30D, AFS40S, AFS40D,AFG30S, AFG30D, AFG40S, AFG40D,AFG81S, AFG81D, AFG82S, AFG82D, AFG83S, AFG83D, AFG84S, AFG84D,AFF50S, and AFF50DSoftware RequirementsThe Ethernet communication module runs on the control functions of the following FCS.LFS1700 Control Function for Field Control Station (for AFV30/AFV40, Vnet/IP and FIO): for AFV30/AFV40LFS1500 Control Function for Field Control Station (for AFV10, Vnet/IP and FIO): for AFV10LFS1300 Control Function for Standard Field Control Station (for V net and FIO): for AFS30/AFS40LFS1330 Control Function for Enhanced Field Control Station (for V net and FIO):for AFG30/AFG40/AFG8 LFS1350 Control Function for Compact Field Control Station (for V net and FIO): for AFF50Engineering RequirementsWorks on LHS5100/LHMS5100 Standard Builder Functio
SUBSYSTEM COMMUNICATIONSThe Ethernet communication module communicates with subsystems at the specified intervals and stores the subsystem data in the communication modules’ I/O image. FCS accesses the communication module asynchronously from them, and refers to or sets the I/O image. This enables FCS to use the subsystem data through the I/O terminals of the function block in the same way as the general analog and digital I/O sign
ORDERING INFORMATIONSpecify the model and suffix codes. For selecting the right products for explosion protection, please refer to TI 33Q01J30-01E without fail. TRADEMARKS• CENTUM, DARWIN, and DAQSTATION are registered trade marks of Yokogawa Electric Corporation.• Ethernet is a registered trade mark of XEROX Corporation.• STARDOM is a trade mark of Yokogawa Electric Corporation.• Modicon and Modbus are registered trade marks of Schneider Electric.• Memocon is a registered trade mark of Yasukawa Electric Co., Ltd.• SLC, PLC-5, and Allen-Bradley are trade marks or registered trade marks of Rockwell Automation, Inc.• MELSEC is a registered trade mark of Mitsubishi Electric Co., Ltd.• Other product and company names appearing in this document are trademarks or registered trademarks of their respective holders.
The Ethernet communication module runs on the control functions of the following FCS.
LFS1700 Control Function for Field Control Station (for AFV30/AFV40, Vnet/IP and FIO):